C22.1-15 - Canadian electrical code, part I (23rd edition), safety standard for electrical installations
Two lists of errata exist for this standard.
Click here to download the errata issued on November 2015
Click here to download the errata issued on August 2016
PrefaceThis twenty-third edition of the Canadian Electrical Code, Part I, was approved by the Committee on the Canadian Electrical Code, Part I, and by the Regulatory Authority Committee at their June 2014 meetings in Victoria, British Columbia. This twenty-third edition supersedes the previous editions, published in 2012, 2009, 2006, 2002, 1998, 1994, 1990, 1986, 1982, 1978, 1975, 1972, 1969, 1966, 1962, 1958, 1953, 1947, 1939, 1935, 1930, and 1927.
This edition features important revisions to many Sections. Section 4 now contains requirements for high-voltage cable ampacities and clarified Rules for conductor termination temperature. In addition, a new table (Table 39) simplifies residential service and feeder conductor selection. More options are provided for load and voltage drop calculations.
Bonding conductor selection has been clarified through the addition of the new Tables 16A and 16B. In addition, Section 12 contains many new and revised requirements for wiring methods, and the conduit fill tables have been expanded.
Section 18 has undergone major revisions. Requirements for Class II and Class III locations have been relocated to Appendix J, and requirements for explosive dust atmospheres based on IEC Zone 20, Zone 21, and Zone 22 have been added to Section 18. The requirements are now located as follows:
Zones 0, 1, 2, 20, 21, and 22 - Section 18
Classes I, II, and III and associated Divisions - Appendix J
Note: References to Class I alone are intended as general references to all classifications of explosive gas atmospheres, Zone 0, Zone 1, and Zone 2.
References to Class II alone or to Class III alone are intended as general references to all classifications of explosive dust atmospheres, Zone 20, Zone 21, and Zone 22.
Specific references to a Zone of a Class I location are references to that Zone.
There are currently no references to Zones or Divisions of Class II or Class III locations in the body of the Rules of this Code (i.e., Sections 0 to 86).
Other revisions in this edition include the following:
Many of the changes in this edition were developed by cross-functional working groups. Their work is gratefully acknowledged.
General arrangementThe Code is divided into numbered Sections, each covering some main division of the work. Sections 0 to 16 and 26 are considered general sections, and the other sections supplement or amend the general sections. The Sections are divided into numbered Rules, with captions for easy reference, as follows:
- Numbering system - With the exception of Section 38, even numbers have been used throughout to identify Sections and Rules. Rule numbers consist of the Section number separated by a hyphen from the 3- or 4-digit figure. The intention in general is that odd numbers may be used for new Rules required by interim revisions. Due to the introduction of some new Rules and the deletion of some existing Rules during the revision of each edition, the Rule numbers for any particular requirement are not always the same in successive editions.
- Subdivision of Rules - Rules are subdivided in the manner illustrated by Rules 8-204 and 8-206, and the subdivisions are identified as follows:
00-000   | Rule
(1) | Subrule
(a)   | Item
(i)   | item
(A)   | item
- Reference to other Rules, etc. - Where reference is made to two or more Rules (e.g., Rules 10-200 to 10-206), the first and last Rules mentioned are included in the reference. Where reference is made to a Subrule or Item in the same Rule, only the Subrule number and/or Item letter and the word "Subrule" or "Item" need be mentioned. If the reference is to another Rule or Section, then the Rule number and the word "Rule" shall be stated (e.g., "Rule 10-200(3)" and not "Subrule (3) of Rule 10-200").
ScopeThis Code covers all electrical work and electrical equipment operating or intended to operate at all voltages in electrical installations for buildings, structures, and premises, including factory-built relocatable and non-relocatable structures, and self-propelled marine vessels stationary for periods exceeding five months and connected to a shore supply of electricity continuously or from time to time, with the following exceptions:
- installations or equipment employed by an electric, communication, or community antenna distribution system utility in the exercise of its function as a utility, as recognized by the regulatory authority having jurisdiction, and located outdoors or in buildings or sections of buildings used for that purpose;
- equipment and facilities that are used in the operation of an electric railway and are supplied exclusively from circuits that supply the motive power;
- installations or equipment used for railway signalling and railway communication purposes, and located outdoors or in buildings or sections of buildings used exclusively for such installations;
- aircraft; and
- electrical systems in ships that are regulated under Transport Canada.
This Code and any standards referenced in it do not make or imply any assurance or guarantee by the authority adopting this Code with respect to life expectancy, durability, or operating performance of equipment and materials so referenced.
About CSA Group
Need more information on any of our products or services? Contact us.
All prices shown are in Canadian dollars (CAD)
Shipping and handling and applicable taxes are added during Check Out.
Product price and availability are subject to change without notice.
Prefer to order offline?